- Very low noise
- Minimal mounting depth
- Functional design
- Time-saving installation
- UV resistant
Filter fans are used to provide an optimum climate in enclosures. The interior temperature of an enclosure can be reduced by channeling cooler filtered outside air into the enclosure thus expelling heated internal air. The resulting air flow prevents formation of localized heat pockets and protects the electronic components from overheating. These filter fans are intended for indoor use. The plastic used for the hood is highly UV light resistant.
Download Operating Instructions
|Axial fan, ball bearing||service life min. 50,000 h at 77 °F (25 °C) and 65 %RH|
aluminum fan body, plastic rotor
|Connection||2 wires w/ cage clamps, AWG 14 (2.5 mm²), length 4” (100 mm)|
|Housing (filter fan and exhaust filter)||plastic, UL 94V-0, light grey|
|Hood (filter fan and exhaust filter)||plastic, UL 94V-0, light grey;|
UV light resistant according to UL 746C (f1)
|Mounting frame||with double-sided industrial adhesive for mounting to the |
outside of enclosure; certain operating circumstances may
make the additional use of screws necessary; cut-out
|Filter media rating||G4 acc. to DIN EN 779, filtering degree 94%|
synthetic fiber with progressive construction, temperature
|Operating / Storage temperature||+14 to +158 °F (-10 to +70 °C ) / -40 to +158 °F (-40 to +70 °C)|
|Operating / Storage humidity||max. 90 %RH (non-condensing)|
|Protection class||I (grounded)|
|Approvals||UL File No. E234324 (all), EAC, VDE (AC 230 V only)|
- The self-adhesive seal of the mounting frame prevents dust and water from entering the cabinet.
- Functional design of the intake and exhaust fan hoods very effectively prevents direct infiltration of falling water and dust. The advantage is that the filter mat does not rapidly become contaminated with dirtand therefore does not need to be exchanged as often.
- The air channeling makes the filter fan particularly quiet in operation.
- The direction of air flow can easily be switched by reversing the axial fan.
- EMC versions and other voltages are available upon request.
Filter Fan FF 018
|Part No.||Operating voltage||Air volume, free blowing||Air volume with exhaust filter||Current consumption||Power consumption||Average noise level (DIN EN ISO 4871)||Mounting depth||Enclosure cut-out||Weight (approx.)||Protection type|
|01800.0-00||AC 230 V, 50 Hz¹||12 cfm (21 m³/h)||9 cfm (16 m³/h)||80 mA||13 W||31 dB (A)||1.8” (45 mm)||3.8 x 3.8”||1.3 lbs. (0.6 kg)||IP54²,|
UL Type 12
|01800.0-01||AC 120 V, 60 Hz||14 cfm (24 m³/h)||11 cfm (18 m³/h)||160 mA||13 W||31 dB (A)||1.8” (45 mm)||3.8 x 3.8”||1.3 lbs. (0.6 kg)||IP54²/IP55³,|
UL Type 12
|01801.0-00||AC 230 V, 50 Hz¹||32 cfm (55 m³/h)||25 cfm (42 m³/h)||100 mA||15 W||40 dB (A)||2.3” (58 mm)||4.9 x 4.9”||2.2 lbs. (1.0 kg)||IP54²/IP55³,|
UL Type 12
|01801.0-01||AC 120 V, 60 Hz||37 cfm (63 m³/h)||28 cfm (48 m³/h)||180 mA||15 W||40 dB (A)||2.3” (58 mm)||4.9 x 4.9”||2.2 lbs. (1.0 kg)||IP54²,|
UL Type 12
|01802.0-00||AC 230 V, 50 Hz¹||60 cfm (102 m³/h)||40 cfm (68 m³/h)||100 mA||15 W||39 dB (A)||3.4” (86 mm)||6.9 x 6.9”||2.9 lbs. (1.3 kg)||IP54²/IP55³,|
UL Type 12
|01802.0-01||AC 120 V, 60 Hz||69 cfm (117 m³/h)||46 cfm (78 m³/h)||180 mA||15 W||39 dB (A)||3.4” (86 mm)||6.9 x 6.9”||2.9 lbs. (1.3 kg)||IP54²/IP55³,|
UL Type 12
1 air volume increases by 15% when operating AC 230 V filter fans at 60 Hz; ² according to VDE; ³ Using fine filter mats type F5/M5 increases the protection type to IP55, but reduces the air volume
Time-saving assembly and maintenance
STEGO's filter fans are easily installed by one person from outside the cabinet.
1.) Make cut-out in the cabinet wall. The cut edge of the cabinet opening should be free of dirt, filings and grease. A template for the enclosure cut-out is included with the filter fan.
2.) Remove protective film from the sealing strips on the mounting frame. Press mounting frame into the cabinet opening. The frame stays permanently in the cabinet.
3.) Electrically connect the axial fan using the cage clamp connectors. Push the unit into the mounting frame. Affix using screws if necessary.
4.) Insert the filter mat in the hood. Clip on. Finished.
To change the filter mat, simply remove the filter hood, insert the new mat and snap the hood back again. No tools are required. Maintenance of the fan can easily be performed without removing the mounting frame (2).
Exhaust Filter EF 118
|Part No.||Mounting depth||Enclosure cut-out||Weight (approx.)||Filter mat||Protection type|
|11800.0-00||0.6” (16 mm)||3.8 x 3.8”||0.6 lbs. (0.3 kg)||G4 acc. to DIN EN 779, filtering degree 94%||IP54²|
|11801.0-00||0.6” (16 mm)||4.9 x 4.9”||0.8 lbs. (0.4 kg)||G4 acc. to DIN EN 779, filtering degree 94%||IP54²/IP55³|
|11802.0-00||0.6” (16 mm)||6.9 x 6.9”||1.3 lbs. (0.6 kg)||G4 acc. to DIN EN 779, filtering degree 94%||IP54²/IP55³|
² according to VDE; ³ Using fine filter mats type F5/M5 increases the protection type to IP55, but reduces the air volume
Filter Mats FM 086 / FFM 086
|Filter mat||3.5 x 3.5” (89 x 89 mm)||4.6 x 4.6” (118 x 118 mm)||6.6 x 6.6” (168 x 168 mm)|
|G4 (1 packing unit = 3 pcs.)||Part No. 08600.0-00||Part No. 08601.0-00||Part No. 08602.0-00|
|F5/M5 (1 packing unit = 3 pcs.)||-||Part No. 08604.0-00||Part No. 08605.0-00|
- Filter Fans>
- FF 018 | 14 cfm to 69 cfm